resistance to earth of a plate R in ohms (code of practice earthing history First published as CP First published as BS BS Code of practice for protective earthing of electrical installations. 16/22 Total Solution to Earthing & Lightning Protection | 9AKKA Technical BS Code of practice for protective earthing of electrical.
|Published (Last):||23 December 2005|
|PDF File Size:||16.35 Mb|
|ePub File Size:||7.42 Mb|
|Price:||Free* [*Free Regsitration Required]|
The resistance to earth of a given electrode depends upon the electrical resistivity of the soil. The basic nature and properties of soil in a given location cannot be changed without considerable expense, and careful consideration of the geology should be used to determine the best location for an earthing system.
It is important to ensure that their resistance areas do not overlap. This may be achieved by making the dimensions in one direction large by comparison to the other two.
The effect of other reinforcement which might be attached by wire ties only, may be neglected.
This is a amendment to a British Standard on how to meet UK electrical installation earthing requirements. Other shapes are not covered here. However, onsite resistivity testing should always be carried out prior to carrying out an earth system design and installation. This website is best viewed with browser version of up to Microsoft Internet Explorer 8 or Firefox 3.
To obtain a low overall resistance the current density eartuing be as low as possible in the medium surrounding the electrode. Earthing systems should consist of copper conductors, copper clad or austenitic steel rods of appropriate dimensions, cast iron plates, or steel piles used individually or connected together in combination to form a single local earth electrode system.
The effect of shape on an electrode resistance is related to the current density around the particular electrode considered. This is one of the rpactice design reference i have seen. It is therefore important to recognize this issue if a long horizontal tape or bare cable is being considered for producing a low earth resistanceeven though the impedance will ultimately be limited to a final value see Figure 4.
It is earthng essential to consider the current density at the surface of the earth electrode and the ground potentials in its vicinity. This applies particularly to surfaces which might have been primed before assembly. Professional in AutoCAD programming. Standard Number BS Take the smart route to manage medical device compliance. The total electrode area formed by the underground metalwork of large structure may often be vs7430 to provide an earth coode lower then that obtainable by other methods.
The finished joint should be covered with a heavy coat of bitumen. The value of resistance required might not always be amenable to an automatically set value. This is related to the hemispherical radius of the rod and that has avoided the effects of using less than the two-times constraint in design thinking.
Premium Membership Get earthjng to premium electrical guides, technical articles cofe much more!
BS +A Code of practice for protective earthing of electrical installations
Wherever significant continuous earth leakage current is expected, it is recommended that a main electrode of the types described in previous section be provided to which the foundation electrodes can be bonded to provide auxiliary electrodes, thus giving assistance to high fault currents.
The majority of the formulae presented in this section relate to low frequency currents and high frequency examples are not included. It also defines selection parameters for the earthing arrangements and makes clear the need for careful consideration of various site conditions od as soil composition and resistivity.
Manish Darji Feb 26, For coode sizes, the resistance is approximately inversely proportional to the linear dimensions, not to the surface areai. They may be used to give an indication of the difficulties that one might face in preparing an adequate design at the chosen location.
This amendment tackles these issues and provides clarification on a number of points in the standard in order to eliminate any ambiguity. In particular, continuous earth currents should be given attention. Plates, if used, should be installed as small units of not greater than 1. You may experience issues viewing this site in Internet Explorer 9, 10 or The resistance R should be taken as the ratio of the voltage between the inner electrodes and the current between the outer electrodes.
There are commercially available materials to achieve this effectively, but care should be taken to understand how they work during installation to ensure that they remain in contact with the rod or strip and do not shrink or swell away after drying out. It includes a number of editorial changes which clarify the meaning of the text and corrects values and symbols.
It is important to ensure electrical continuity between all metalwork considered to be part of the electrode. Accept and continue Learn more about the cookies we use and how to change your settings.
The resistivity found applies to soil depth a, so by repeating the measurement with different values of athe average resistivity to various depths may be found and the results indicates whether any advantage is to be gained by installing deeply driven electrodes in order to reach strata of a lower resistivity.
earrthing This should include the size and shape of the earth conductor, the resistivity of the soil in which it is buried and the connection of the system to it.
Find Similar Items This product falls into the following categories. This situation is unlikely to arise if the electrode has a resistance sufficiently low to avoid dangerous voltages to earth.
Measurements and Calculations Of Earth Electrode Systems (BS ) | EEP
Chemical treatment of soil has environmental implications and should not be considered as a long term solution in order to meet a specified level of resistance, apart from the risk of corrosion to the earthling system. Where the structure is supported on many similar footings, it may be considered feasible and more satisfactory to measure the resistance of one footing before it is electrically connected to othersand before there are any other electrically paralleled footings close by.
The content is copyrighted to EEP and may not be reproduced on other websites.
Soil resistivity may be measured in a similar manner to the establishment of the resistance of the earth electrode. This section deals only with a straight run of conductor. Search all products by. This model is more closely aligned to the basic theory behind the electrostatic behaviour of an earthing system componentin effect stating more clearly the interactive effect of the value of s which for practical purposes has long been set as being not less than twice the depth of the rod.
Therefore any part of an electrode system which is less that 0. You may find similar items within these categories by selecting from the choices below:. In the case of contacts between metalwork within concrete or below ground, such as reinforcing bars, this may best be effected by welding.